The zinc oxide arrester is equipped with an online leakage current meter to monitor the operation of the arrester. The online leakage current meter reflects the current of the insulation and arrester discs through the porcelain shell.
(1) the online leakage current meter reading of the arrester increases significantly. The moisture in the arrester is mainly caused by poor sealing. The source of moisture is: in the production process of the arrester, the installation environment humidity exceeds the standard; The valve disc and internal parts are not thoroughly dry, and there is partial moisture retention; When assembling, leak the sealing ring and deflect; Or between the sealing ring and porcelain sleeve sealing cover between the sundries; After a period of operation, the sealing parts are damaged.
(2) the online leakage current meter reading of the arrester is reduced or even zero.
Zhejiang Gaoneng Electric Installation Co., Ltd.
Address: JieDai Industrial Zone, Yueqing, 325600, Zhejiang, China
Contact: Mrs Smiler
Mobile: +86 13666634915
- Composite Insulator Classification
- The History Of Composite Insulators
- The Role Of Insulators
- Structure And Characteristics Of Composite Insu...
- Insulators Shipped To Turkey
- Vietnamese Customers Visit Lishui Factory
- Composite insulators shipped to Kenya
- Insulator Inspection
- Develop New Equipment
- How Does The Composite Insulator Resist Pollution?
- What Are The Advantages Of Composite Insulators?
- Composite Insulators In The Transmission Line W...
- Composite Insulator Tensile Testing Machine Str...
- China's Composite Insulator Industry Market Dev...
- Insulator Arrester Industry Development Researc...
- Composite Insulator Main Application Field
- What Role Do Composite Insulators Play In Trans...
- Selection Of Mechanical Intensity Of Composite ...
- How To Judge The Voltage According To The Insul...
- Advantages Of Composite Insulators (1)